Building Design Requirements
|Current Adopted Building Codes|| 2013 Edition California Building Code
2013 Edition California Electrical Code
2013 Edition California Energy Code
2013 Edition California Mechanical Code
2013 Edition California Plumbing Code
1997 Edition Uniform Housing Code, Chapter 4, 5 & 6 and Sections 701.2 and 701.3
2012 Edition Uniform Swimming Pool, Spa and Hot Tub Code 2010 County of Los Angeles Fire Code
|Structural References|| ASCE 7-10 AISC 360-10 & 341-10, ACI 318 -11, TMS 402-11, NDS- 12 and others as identified in the Building Code
|Seismic Design – See CBC Section 1613 and ASCE 7-05 Chapter 11, 12 & 20.|| Site class: Site class D is assumed unless soils report specifies otherwise.
Seismic Design Category: E or F. Go to http://earthquake.usgs.gov/research/hazards/designmaps/ to determine S1 and Ss.
|Wind Design|| Basic Wind Speed:
Risk Category I - 100 MPH
Risk Category II- 110 MPH
Risk Category iii & Iv - 115 MPH
Importance factor, exposure and topographic features are site and project specific. See ASCE 7-10, Chapter 6.
|Soil and Foundation||Foundation and soils investigation and reports are required per CBC Section 1802.2.|
|Climate Zone||Climate Zone 9|
|Very High Fire Severity Zones||Yes, areas of Azusa are located within VHFSZ. Go to Cal Fire to determine if site is located in VHFSZ.|
|Seismic Hazard Zones||Yes, areas of Azusa are located in Seismic Hazard severity zones prone to Liquefaction and/or Landslides. Go to SHZP Data Maps to determine if site is located in Seismic Hazard Zone.|
|Additional Information||Additional design information can be found in Chapter 14 of the City of Azusa Municipal Code.|